Questions about repairs and parts for other brands of furnaces and air conditioners. Please note that our speciality is Coleman and Nordyne products, so our knowledge of other brands may be limited.
Moderators: ponch37300, Mark, flcruising, Greg
I am having a couple of problems 1) the furnace will come on blower first before the elements and they sometimes do not heat up and will have to shut off and back to get them to heat up. 2) the elements themselves are a double stack and only half of each element (the very ends) will heat up I don't know what might these 2 problems and if they are related to each other.I have replaced all 4 fuses and that did not seem to help any ideas thank you,Nina.
- Posts: 1
- Joined: Fri Dec 11, 2009 12:53 pm
Could be a bad sequencer or an element going bad.
Would need to test for voltage to elements, amp draw for each element and return and supply temp from furnace return grille and nearest supply register to furnace.
Some people are Humbly Grateful, while some are Grumbly Hateful.................... Which one are you ?
- Posts: 6413
- Joined: Wed Feb 28, 2007 12:07 am
- Location: Tennessee
Return to Service & Repair of Other Brands
Who is online
Users browsing this forum: No registered users and 1 guest